## Navigation

- FAQ Home
- All categories
- Instructions
- Section 1.0 - General
- Section 2.0 - Loads
- Section 3.0 - Analysis
- Section 4.0 - Design Strength of Structural Steel
- Section 5.0 - Manufacturing
- Section 6.0 - Other Structural Materials
- Section 7.0 - Guy Assemblies
- Section 8.0 - Insulators
- Section 9.0 - Foundations and Anchorages
- Section 10.0 - Protective Grounding
- Section 11.0 - Obstruction Marking
- Section 12.0 - Climbing Facilities
- Section 13.0 - Plans, Assembly Tolerances and Marking
- Section 14.0 - Maintenance and Condition Assessment
- Section 15.0 - Existing Structures
- Section 16.0 - Installation
- Annex A: Procurement and User Guidelines
- Annex B: U.S. Country Listings of Design Criteria
- Annex C: Design Wind Force on Typical Antennas
- Annex D: Twist and Sway Limitations for Microwave Antennas
- Annex E: Guy Rupture
- Annex F: Presumptive Soil Parameters
- Annex G: Geotechnical Investigations
- Annex H: Additional Corrosion Control
- Annex I: Climber Attachment Anchorages
- Annex J: Maintenance and Condition Assessment
- Annex K: Measuring Guy Tensions
- Annex L: Wind Speed Conversions
- Annex M: SI Conversion Factors
- Annex N: References
- Appendix 1: Design Criteria Maps
- TIA-222-F
- Miscellaneous
- Rejected Questions
- TIA-1019-A/TIA-322
- Sitemap

40 users online :: 40 Guests and 0 Registered

### Records in this category

- Section 9.6 What is the intent of the grade beam, similar device, or other approved method to resist a portion of the base seismic shear? Is it to resist differential foundation displacements during a seismic event, to resist the effects of liquefaction, or both? If differential displacements is a concern, what is the allowable displacement? Does the same force requirement (2/3 of the total base shear) apply for 3-legged and 4-legged structures alike?
- I’m trying to determine if a pad & pier should use a phi of 0.75 on the resisting moment to resist overturning. Mult/(Phi*Mrest)I believe it is the intent of the TIA to say this (per 9.4) but it is not explicit.If the phi is to be included in the overturning calculation; Then does it apply to the entire resisting moment or just the portion derived from the soil (as opposed to the foundation weight or axial weight?

### Tags

### Sticky FAQs

- How do I use this Site?
- Do we have to do a structural analysis on ...
- Does the Standard apply to the design of antennas? ...
- How to submit a question?
- Section 2.6.9.2What does the term “In the absence of ...
- Section 2.6.9.2Is it acceptable to use the results of ...
- Section 2.6.9.2Can I use loading that is less than ...
- Section 2.6.9.2Is it acceptable to use the results of ...
- Section 13.3 question regarding plumb measurement of monopoles; submitted ...
- Figure A1-1 Why were the tables and Note 3 ...
- 1) I knew this table 4-8 is used to ...
- 2.6.7.4 Gust Effect Factor for Structures Mounted on Other ...
- Is there reciprocity between ANSI/TIA-222-G and CSA S37-01? In ...
- Section 15.5 indicated "A feasibility report shall state ...
- Section 2.6.6 Calculating the topographic factors
- As everyone is aware, many jurisdictions are now adopting ...
- Section 2.7.3 states “Further, …earthquake effects may be ignored ...
- I am currently working a telecommunications tower project where ...
- Is there a tolerance recommendation for base plate to ...
- in case of telecommunication tower to be built on ...
- Is there a tolerance recommendation for base plate to ...
- in case of telecommunication tower to be built on ...
- The definition of Z in sections 2.6.5.2, 2.6.6.4, and ...
- If Ca=1.5 is used for a rectangular cluster of ...
- Section 2.6.5.2 “Velocity Pressure Coefficient”Question: Shall “z” in the ...
- Section 4.9.9: I'm using this section to calculate the ...
- Section 2.6.6.4 - Rev-G provides a simplified method of ...
- WHICH IS THE unbraced length "L" TO CONSIDER, ACCORDING ...
- Does section 2.8.2 Limit State Deformations of ANSI/TIA 222-G ...
- Where it has been suggested in previous posts that ...
- We understand section 2.6.4.1 to apply only to areas ...
- Waveguides, downleads, and other cables are frequently strapped to ...
- Should step pegs and safety climb be included in ...
- Section 3.6.2 note 1 regarding pattern loading and tower ...
- Approximately when will the next revision or amendment to ...
- I have a tower for which the plumb and ...
- In Section 4.4.1 of TIA/EIA-222-G December 2009 the minimum ...
- Section 3108.1 of the 2012 IBC eliminates the 222-G ...
- Section 9.6 What is the intent of the grade ...
- One thing I recently noticed was in Table C1, ...
- Regarding recent FAQ 1128: would it be possible to ...
- I’m trying to determine if a pad & pier ...
- Is it the intention of drafters of the TIA ...
- Section 2.6.5: Addendum 2 defines Exposure Category C as ...
- Section 5.4.2 gives requirements for Non Pre-Qualified Steel stating ...
- Which of the states adhere to the Rev G ...
- In Section 4.5.1, the following language is used:"A multiple ...
- Shall “z” in the equation be based on mid-height ...
- Section 4.9.9: I’m using this section to calculate the ...
- Section 2.6.6.4 - Rev-G provides a simplified method of ...
- Which is the unbraced length to consider, according to ...
- I am a commercial building reviewer for the City ...
- Does section 2.8.2 Limit State Deformations of ANSI/TIA 222-G ...
- Can section 2.8.2 also be applied to a TIA-222-F ...
- Table 4-6 provides slenderness requirements for horizontal members, specifically ...
- Where it has been suggested in previous posts that ...
- One thing I recently noticed was in Table C1, ...
- In Section 4.5.1, the following language is used:"A multiple ...
- Is it acceptable to use Ka = 0.6 for ...
- For double angles, are the modified (KL/r)m equations shall ...
- K is not mentioned on the right side of ...
- Is (KL/r)o shall include the curves defined in Table ...
- Section 4.9.8. Does the definition of Guy Assembly Link ...
- Section 12 Climbing Facilities in TIA-222-GWhat is the strength ...
- Section 12 Climbing Facilities TIA-222-GWhat is the strength requirement ...
- Section 4.5.3 Built-Up Members states that "A minimum of ...
- Referencing Section 2.3.2, Exception 4 and Note 3; for ...
- Is there any back up material for the usage ...
- I am a structural engineer in Oregon, and I ...
- Section 2.6.1: In the definitions section of 2.6.1, a ...
- Does TIA-222-G include any consideration of loads other than ...
- Should mounts be subjected to Section 15 requirements that ...
- Hello,The effective projected area of transmission lines mounted in ...
- Section 2.6.9My question is regarding how to determine the ...
- Hello. A question was asked about the validity of ...
- The inspection intervals are recommended. Can I extend the ...
- Is there any available document or article that explains ...
- Section A.2.2 and Table 2-1 establish the classification of ...
- Section A.2.2 and Table 2-1 establish the classification of ...
- The industry is on the verge of the release ...

## Section 9.0 - Foundations and Anchorages

ID #1142

## I’m trying to determine if a pad & pier should use a phi of 0.75 on the resisting moment to resist overturning. Mult/(Phi*Mrest)I believe it is the intent of the TIA to say this (per 9.4) but it is not explicit.If the phi is to be included in the overturning calculation; Then does it apply to the entire resisting moment or just the portion derived from the soil (as opposed to the foundation weight or axial weight?

The resistance factor ( = 0.75) is intended to apply to only the soil resistance related to soil strength, as opposed to soil overburden weight directly above the foundation. The total overturning resistance of the foundation is a function of the soil resistance, the weight of the foundation and soil overburden and the factored axial load. It would not be appropriate to apply an additional 0.75 resistance factor to the total overturning resistance calculated in this manner. Note that the foundation and soil overburden weight are considered as dead load with the load factors of 0.90 or 1.20 per Section 2.3.2 (specifically Note 3).

**Tags: ** -

**Related entries: **

- Some antenna manufacturers provide flat equivalent area and few of them just provide the dimensions. How can we address the CaAa without ice and with ½” ice for discrete appurtenance without flat equivalent area known?s
- How can we include the CaAa with ½” ice for dipoles and yagi’s?
- For triangular towers: How can we calculate the Df for other wind directions such as 30 and 45 degrees?
- 2.6.9.1.1 For square towers: How can we calculate the DF and DR factors for other wind directions?
- Section 2.6.9.2What does the term “In the absence of more accurate data” mean?
- Section 2.6.9.2Can I use loading that is less than the values prescribed by the written TIA-222-G and claim compliance with the standard? If so, under what conditions?
- Does the Standard apply to the design of antennas?
- Section 4.6.3.2 question regarding shear lag factor; submitted 9/15/2010
- Section 15.4 question regarding Changed Conditions Requiring a Structural Analysis; submitted 2/14/2007
- Section 15.4 question regarding existing tower re-analysis; submitted 12/31/2007

Author: John Erichsen

Revision: 1.1

You cannot comment on this entry